The Developer shall adhere to all safety rules, regulations and requirements of local authorities whatever it may be applicable to the construction site. The Developer shall follow all safety procedures prescribed in the AGC (American General Developer's) Manual of Accident Prevention in Construction, Occupational Safety and Health Administration (OSHA) of USA and all other local codes and regulations.
This method of statement specifies the detailed requirements and procedures for the installation of Power and Lighting System Wiring. Installation: No wiring be carried out until the appropriate tests required or in the electrical testing section have been done and the consultant has given his clearance for wiring to commence. A loop in form of wiring shall be used as far as practicable or unless otherwise indicated. Joints in conductors shall be made using insulated terminal blocks complying with requirements of this specification.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here. This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls. This method statement should be used for both inside and out side the building.
This method statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB Panelboards.
Electrical Engineers seldom show interest acquiring knowledge and experience on cable tray installations. Most of them think it's a concern of mechanical fabricators to be taken care of it. A proper and professional way of cable tray installation requires good involvement and coordination of people from both electrical and mechanical disciplines. If cable tray system has been installed appropriately in a project, following advantages can be counted:
Every project is unique, in particular, construction projects. There are many methods applied to accomplish functioning of individual installations included in the whole project. Building services like Mechanical, Electric, and Plumbing (MEP) work have given more importance than other disciplines dealt with. It's because of complexity and alternate methods available to accomplish the same output. While executing individual installations - also known as tasks - construction team have to adopt suitable methods submitted as an integral part of Tender.
Modern Buildings essentially implement the needs of Diesel Powered Electricity Generation Plant. It would become an integral part of the building the day building occupied by its tenants. Here we look into what are the objectives, specifications, services to be considered for functioning complete Diesel Powered Electricity Generation Plant installed in a commercial Building.
The DC power supply shall consist of batteries and batteries charger.
Batteries of DC Power Supply - Technical Specifications
The batteries shall be nickel cadmium type with pocket plates type range TP, T.
The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
In this sample MEP specification section, Air Conditioning And Ventilation Installations have been described in detail under construction contract work. All individual components of packaged air handling units shall comply with the appropriate Sections of this Specification unless otherwise specified within the Schedules or on the drawings.