Modern Buildings essentially implement the needs of Diesel Powered Electricity Generation Plant. It would become an integral part of the building the day building occupied by its tenants. Here we look into what are the objectives, specifications, services to be considered for functioning complete Diesel Powered Electricity Generation Plant installed in a commercial Building.
The metallic sheath and armour of multicore cables shall be bonded together and earthed. Cable earthing conductors shall be copper strip with appropriate section laid in formed cable trenches or ducts, or fixed to walls, concrete or steel work, by means of clamps or claw type cleats, appropriately secured into suitable wall plugs or tapped holes. The spacing of fixings shall not be greater than 1 m.
Electrical engineering deals with practical applications involving current flow through conductors; focuses on the design, construction, and operation of electrical systems and equipment. It includes developing, producing and testing of electrical and electronic devices and equipment, such as, generators to produce and distribute electricity, electric motors and other electrical machinery, transmission line.
Scope of Work of this this sample specification covers the supply, installation, testing and commissioning of all wiring materials for power and lighting in concealed and/or surface conduits.
1. Applicable Standards
The conduits shall conform to IS 9537 I & II or equivalent standards. Switches, Plug Sockets shall conform to IS 3854 and IS 4615, however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here. This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Lightning Protection System should be in accordance with BS 6651 and IEC 61024 to protect the building structure and personnel from the risk of a lightning strike. The installation shall comprise air networks connected to roof and down conductors and finally terminated in earth electrodes, via structural re-bars and suitable test points in accordance with the details included on the attached drawings or in the Specification Section.
In electrical projects, both construction as well as maintenance, the following terms used on the Drawings, Specifications and in the actual Work site are equivalent and may be used interchangeably: "earth" and "ground"; "earthing" and "grounding". Besides, this article tries to rectify misinterpretation of some important terms often used by people involved in the electrical earthing / grounding work.
A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).