These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors.
Engineering and Technologies are, in the first instance, simply extensions of the human body, allowing us to overcome the physical limitations with which we are born, and to adapt the natural environment to our own needs. Technologies are inventions of humans that have allowed us to survive, and have enabled our cultures to advance. They are for the most part material objects: tools, for example, are simply detachable additions to the body, the manufacture of which generally distinguishes humans from animals.
Reliable electrical power becomes one of the most wanted factor in modern world industry where operation should be uninterruptible and maximize the cycle of operation, output quality and to avoid losses and damages. Here we are talking about Automatic Transfer Switches (ATS) also known as Automatic Mains Failure (AMF) panel to cater uninterrupted power supply from Mains or backup sources like Diesel gen-set, static ups etc.
We often depends Diesel Electrical Genset as emergency power system due to mains failure. As a professional, the installation of diesel electrical power generator should be as per the clients requirement and to be inline with the authoritative norms and standards. Safety, security, convenience, future expansions etc are to be considered and co-ordinated before start detailing of the genset's installation. The generator should be as close to the main change-over board as possible. In cases like Textile Mills, where there is fear of smoke affecting the quality of the yarn etc., generators may be located away from the Plant / Department.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
Electrical wiring needs expertise attention to every building projects. It directly related to the safety of human beings and utilities / equipment people handle. The scope of electrical wiring shall cover supply, installation, testing and commissioning of all conduits and accessories, wiring, switches, socket outlets, junction boxes / pull boxes, GI pull wires, ceiling roses making connections etc. Unless otherwise indicated wiring shall consist of PVC insulated copper conductor wires installed in heavy gauge steel galvanized conduits.