The metallic sheath and armour of multicore cables shall be bonded together and earthed. Cable earthing conductors shall be copper strip with appropriate section laid in formed cable trenches or ducts, or fixed to walls, concrete or steel work, by means of clamps or claw type cleats, appropriately secured into suitable wall plugs or tapped holes. The spacing of fixings shall not be greater than 1 m.
A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
It is essential that services and systems in a building construction contract work are provided to conform to the requirements of the customer, and that the activities be effected as economically as practical. The achievement of these objectives is facilitated by setting up working procedures and practices, which collectively provide a “Work Efficient”, yet controlled operating environment. It is the purpose of this Construction Quality Plan to give instruction to personnel, on the implementation of the company system such that the above objectives are accomplished. Documentation specific to the project will be provided to ensure full compliance with the particular requirements of the contract.
The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
Low Voltage Switchgear are familiar to every people since they are the controlling mediators between low voltage utilities and equipment with human beings. Be it a common home DB or an isolator or control centres, they all are being manufactured to use untrained people ie., common people. The scope of works shall cover the supply installation, testing and commissioning of main and sub-distribution boards, panel boards, fusible safety switches, circuit breakers etc. Associated minor building works require for the erection of the distribution boards and panels shall be included in the scope of work.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.