Most electronic systems which are responsible for modern advances are based on digital technology. All digital systems, computers and microprocessors are assembled from simple circuits called logic circuits. The basic building blocks of logic circuits are logic gates. And logic gates themselves are simple electronic circuits comprising of diodes, transistors and resistors.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.
Most Construction projects requires underground cabling system for its power supply, some times High tension system too. The architects and builders are least bothered about how this cables routed to the premises and equipment. If electrical professionals pointed out the feasibility, the aesthetics of the project would touch to the intended level. Hence, in the planning stage itself the routes and size of the power cable trench to be incorporated in the project design.
At the completion of the electrical installation works, the entire installation shall be subject to the test before final placing in service under the full responsibility of the contractor. Unless Otherwise specifically called for all tests shall be carried out in conformity with IEE regulations. Contractor shall coordinate with the Client and the Supervising Engineer to get electricity from the local supply authority before starting of testing and commissioning.
Electrical wiring needs expertise attention to every building projects. It directly related to the safety of human beings and utilities / equipment people handle. The scope of electrical wiring shall cover supply, installation, testing and commissioning of all conduits and accessories, wiring, switches, socket outlets, spur outlets, junction boxes / pull boxes, GI pull wires, ceiling roses making connections etc. This Electrical Construction Article gives comprehensive details of various installation methods, materials used in each installation methods used in building construction projects.
The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
1. Introduction and Scope
This method of statement specifies the detailed requirements and procedures for the installation of Power and Lighting System Wiring.
2. Applicable Project Specification
Section: Cables and wiring
Sub Division: Subdivision
Electrical Engineers seldom show interest acquiring knowledge and experience on cable tray installations. Most of them think it's a concern of mechanical fabricators to be taken care of it. A proper and professional way of cable tray installation requires good involvement and coordination of people from both electrical and mechanical disciplines. If cable tray system has been installed appropriately in a project, following advantages can be counted:
- Cable Tray system enhances safety of electrical wiring system.
- Cable tray installation provides dependability in any circumstances.
- Cable Tray system saves space, materials, labor, time and cost.
- Maintenance and extension of cable tray installation are easier than any other wiring system.
Hence, electrical installation of a project must give high priority to adopt properly evaluated cable tray wiring system if aesthetic impact is low. This article explains how to make a typical method statement for cable tray or trunking installation for a building project.
Below drawing shows how to install cable tray and its support system. This cable tray support system drawing has Isometric view and cross-sectional view. Following are the steps to be done for laying cables on wall mounted cable tray:
- Install cable tray support using a pre-fabricated flange or GI channel. The size, length and intervals of the support to be as per the specification, standards, number of cables, and size of the cable.
- Fix the cable tray as shown on the drawing.
- Lay the cable keeping the distance as per calculation.
- Tie the cable using cable tie and label the cables as required.
Method Statement For Installation Of Electrical PVC Conduits And Accessories In The Concrete Slabs, Columns, Block Works And Concrete Walls
1. Introduction and Scope
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls.
Reliable electrical power becomes one of the most wanted factor in modern world industry where operation should be uninterruptible and maximize the cycle of operation, output quality and to avoid losses and damages. Here we are talking about Automatic Transfer Switches (ATS) also known as Automatic Mains Failure (AMF) panel to cater uninterrupted power supply from Mains or backup sources like Diesel gen-set, static ups etc.
What is Automatic Transfer Switch (ATS)?Automatic Transfer Switch (ATS) is an automated switching device that transfers load power to backup power during mains failure and back to its original state when mains power reinstate to the normal condition. It will have its own contacts, microprocessor to analyses the conditions whether power supply is normal or backup and need backup or mains power. Here "back up power" may become either Standby generator or another mains power or static power source like UPS.
Scope of Work of this this sample specification covers the supply, installation, testing and commissioning of all wiring materials for power and lighting in concealed and/or surface conduits.
1. Applicable Standards
The conduits shall conform to IS 9537 I & II or equivalent standards. Switches, Plug Sockets shall conform to IS 3854 and IS 4615, however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Electrical Sub-Main Distribution Boards (SMDB) are the integral part of Electrical LV Power distribution network in the end user premises of a medium and large scale projects. SMDB acts as a mediator between Main Distribution Board (MDB) and Final Distribution Boards (FDB) that serves approximately 100A to 400A load range.
Method of Earthing To Main Distribution Board (MDB)
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.
Fire alarm systems have become increasingly sophisticated and functionally more capable and reliable in recent years. They are designed to fulfill two general requirements: protection of property and assets and protection of life. As a result of state and local codes, the life-safety aspect of fire protection has become a major factor in the last two decades.
Lighting Distribution Boards (LDB) are an integral and essential part of every building project and it must be designed, manufactured and installed all in accordance with the safety standards. In most of the cases it operates a layman wherein others operate dedicated or trained person. This article explains what are the essential standards, parts, frame to be applied for manufacturing and installation of lighting distribution boards in a quality building project.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors. Conduit end to be taken out of the wall above false ceiling to allow the Firetuff cable to be clipped on soffit of the slab.
Drawing below shows how to install Manual call point break glass along with a sounder
In this typical drawing, manual call point break glass unit has been shown as concealed and the rest are surface installed in the false ceiling. Sounder has been mounted on ceiling but can also be mounted on wall visibly as per the project specification.
The value is a function of cost. Therefore, it can be increased either by improving the function or reducing cost. The maximum value is achieved when the function performs reliably at the lowest cost. A key principle of value engineering that basic functions be preserved and not reduced as a result of improvements in value. Thus Value Engineering (VE) is a systematic method to improve the "value" of goods, products or services through an examination of the function.
Component parts of earthing system are to include the following:
- Earth electrode (rods, tapes etc.)
- Main earthing terminals or bars
- Earthing conductors
- Protective conductors
- Equipotential bonding conductors
- Electrically independent earth electrodes for special systems (clean earth)
- Accessories and termination fittings, bonding, welding kits and other materials
Comply with the General Conditions, Supplementary Conditions and the requirements in various Sections of the Electrical Specification. In addition read and conform to all Electrical Sections of these specifications. The installation shall comprise air networks connected to roof and down conductors and finally terminated in earth electrodes, via structural re-bars and suitable test points in accordance with the details included on the attached drawings or in the Specification Section.