Most electronic systems which are responsible for modern advances are based on digital technology. All digital systems, computers and microprocessors are assembled from simple circuits called logic circuits. The basic building blocks of logic circuits are logic gates. And logic gates themselves are simple electronic circuits comprising of diodes, transistors and resistors.
At the completion of the electrical installation works, the entire installation shall be subject to the test before final placing in service under the full responsibility of the contractor. Unless Otherwise specifically called for all tests shall be carried out in conformity with IEE regulations. Contractor shall coordinate with the Client and the Supervising Engineer to get electricity from the local supply authority before starting of testing and commissioning.
1. Introduction and Scope
This method statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB Panelboards.
2. Applicable Projects Specification
Section: SWITCHBOARD DISTRIBUTION PANELS AND MCCs.
Sub Division: Subdivision
3. Location of Activity
Low Voltage Room and Electrical Rooms
The contractor shall supply, install, test and commission the 13.8 KV cable network as shown and indicated on the contract documents. Conductor sizes shall be metric as shown, conductor sizes with cross sectional areas smaller than specified will not be accepted. The cable installation shall include all trench work, sleeves, ducts, and all necessary fixings and cable terminations at both ends of the cable. The contractor shall supply and install cable marker posts to indicate the route of all underground cables. Markers shall be provided at every bend along the route and at sites of crossing roads or pipe lines.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.
Most Construction projects requires underground cabling system for its power supply, some times High tension system too. The architects and builders are least bothered about how this cables routed to the premises and equipment. If electrical professionals pointed out the feasibility, the aesthetics of the project would touch to the intended level. Hence, in the planning stage itself the routes and size of the power cable trench to be incorporated in the project design.
It will be the Developers responsibility to obtain all necessary approvals from Authorities having jurisdiction for temporary connections to existing infrastructure. Temporary utilities shall be installed in such a manner as not to interfere with permanent construction. The Plot Developer shall provide any temporary holes or sleeves required to install the temporary utilities and shall be responsible to fill the same upon removal of utilities.
Electrical wiring needs expertise attention to every building projects. It directly related to the safety of human beings and utilities / equipment people handle. The scope of electrical wiring shall cover supply, installation, testing and commissioning of all conduits and accessories, wiring, switches, socket outlets, spur outlets, junction boxes / pull boxes, GI pull wires, ceiling roses making connections etc. This Electrical Construction Article gives comprehensive details of various installation methods, materials used in each installation methods used in building construction projects.
Method of Earthing To Main Distribution Board (MDB)
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.
Occasionally Main Contractor of the construction work depends sub-contractor for accomplishing some smaller or part of the project that may require specialized technical know-how and installation methods. In those cases Main contractor selects some sub-contractors who has capacity to achieve the task within the given time frame. Hence both of the parties, ie., Main contractor and Sub-contractor to be signed an agreement which protects both the parties' interest. Here is a sample for Conditions of Sub-contract Agreement in Construction Works.
Component parts of earthing system are to include the following:
- Earth electrode (rods, tapes etc.)
- Main earthing terminals or bars
- Earthing conductors
- Protective conductors
- Equipotential bonding conductors
- Electrically independent earth electrodes for special systems (clean earth)
- Accessories and termination fittings, bonding, welding kits and other materials
We often depends Diesel Electrical Genset as emergency power system due to mains failure. As a professional, the installation of diesel electrical power generator should be as per the clients requirement and to be inline with the authoritative norms and standards. Safety, security, convenience, future expansions etc are to be considered and co-ordinated before start detailing of the genset's installation. The generator should be as close to the main change-over board as possible. In cases like Textile Mills, where there is fear of smoke affecting the quality of the yarn etc., generators may be located away from the Plant / Department.
Comply with the General Conditions, Supplementary Conditions and the requirements in various Sections of the Electrical Specification. In addition read and conform to all Electrical Sections of these specifications. The installation shall comprise air networks connected to roof and down conductors and finally terminated in earth electrodes, via structural re-bars and suitable test points in accordance with the details included on the attached drawings or in the Specification Section.
Lighting Distribution Boards (LDB) are an integral and essential part of every building project and it must be designed, manufactured and installed all in accordance with the safety standards. In most of the cases it operates a layman wherein others operate dedicated or trained person. This article explains what are the essential standards, parts, frame to be applied for manufacturing and installation of lighting distribution boards in a quality building project.
Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
Earthing or Grounding Electrode for an effective and reliable electrical earthing system requires proper survey and analysis of project location, type of structures installed and electrical / electronic equipment used in the entire system. The design calculation of the earth electrode systems shall be based on the approved earth resistivity data and the system's fault currents and their duration.