Most Construction projects requires underground cabling system for its power supply, some times High tension system too. The architects and builders are least bothered about how this cables routed to the premises and equipment. If electrical professionals pointed out the feasibility, the aesthetics of the project would touch to the intended level. Hence, in the planning stage itself the routes and size of the power cable trench to be incorporated in the project design.
Most electronic systems which are responsible for modern advances are based on digital technology. All digital systems, computers and microprocessors are assembled from simple circuits called logic circuits. The basic building blocks of logic circuits are logic gates. And logic gates themselves are simple electronic circuits comprising of diodes, transistors and resistors.
At the completion of the electrical installation works, the entire installation shall be subject to the test before final placing in service under the full responsibility of the contractor. Unless Otherwise specifically called for all tests shall be carried out in conformity with IEE regulations. Contractor shall coordinate with the Client and the Supervising Engineer to get electricity from the local supply authority before starting of testing and commissioning.
Scope of Work of this this sample specification covers the supply, installation, testing and commissioning of all wiring materials for power and lighting in concealed and/or surface conduits.
1. Applicable Standards
The conduits shall conform to IS 9537 I & II or equivalent standards. Switches, Plug Sockets shall conform to IS 3854 and IS 4615, however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipment luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipment, control gears and poles.
In this sample MEP specification section, Mechanical Fire Fighting Services have been described in detail under construction contract work. Main Highlights of this MEP Specification for Fire Fighting Services are: Pipework Generally, Dry Risers, Hose Reels, Fire Hydrants and Sprinkler Installation.
Component parts of earthing system are to include the following:
- Earth electrode (rods, tapes etc.)
- Main earthing terminals or bars
- Earthing conductors
- Protective conductors
- Equipotential bonding conductors
- Electrically independent earth electrodes for special systems (clean earth)
- Accessories and termination fittings, bonding, welding kits and other materials
The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
Master Antenna Television or MATV means many TV connection outlets from one Master antenna control system. Usually high-rise apartment houses, hotels, schools and cluster based residential area utilizes this kind of TV distribution network. It may or may not include FM radio so that one outlet can receive both TV and FM reception. The scope of this section covers the design, supply, installation, testing and commissioning of Master Antenna TV System, for the reception and distribution of television broadcast signals.
A. Earthing Cables: Separate protective earthing cables for lighting column circuits are to be run with power circuit, terminated at LV supply position in lighting control panel and looped into column earthing terminals. The last column is to be bonded via an earthing bolt to a single 16 mm diameter stainless steel rod, 3.6 m long, driven into ground adjacent to column. Bonding is to be 16 mm2 stranded bare copper conductor.
Electrical Engineers seldom show interest acquiring knowledge and experience on cable tray installations. Most of them think it's a concern of mechanical fabricators to be taken care of it. A proper and professional way of cable tray installation requires good involvement and coordination of people from both electrical and mechanical disciplines. If cable tray system has been installed appropriately in a project, following advantages can be counted:
- Cable Tray system enhances safety of electrical wiring system.
- Cable tray installation provides dependability in any circumstances.
- Cable Tray system saves space, materials, labor, time and cost.
- Maintenance and extension of cable tray installation are easier than any other wiring system.
Hence, electrical installation of a project must give high priority to adopt properly evaluated cable tray wiring system if aesthetic impact is low. This article explains how to make a typical method statement for cable tray or trunking installation for a building project.
Below drawing shows how to install cable tray and its support system. This cable tray support system drawing has Isometric view and cross-sectional view. Following are the steps to be done for laying cables on wall mounted cable tray:
- Install cable tray support using a pre-fabricated flange or GI channel. The size, length and intervals of the support to be as per the specification, standards, number of cables, and size of the cable.
- Fix the cable tray as shown on the drawing.
- Lay the cable keeping the distance as per calculation.
- Tie the cable using cable tie and label the cables as required.
Lighting Distribution Boards (LDB) are an integral and essential part of every building project and it must be designed, manufactured and installed all in accordance with the safety standards. In most of the cases it operates a layman wherein others operate dedicated or trained person. This article explains what are the essential standards, parts, frame to be applied for manufacturing and installation of lighting distribution boards in a quality building project.
Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
1. Introduction and Scope
This method statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB Panelboards.
2. Applicable Projects Specification
Section: SWITCHBOARD DISTRIBUTION PANELS AND MCCs.
Sub Division: Subdivision
3. Location of Activity
Low Voltage Room and Electrical Rooms
Earthing or Grounding Electrode for an effective and reliable electrical earthing system requires proper survey and analysis of project location, type of structures installed and electrical / electronic equipment used in the entire system. The design calculation of the earth electrode systems shall be based on the approved earth resistivity data and the system's fault currents and their duration.