Particular Specification For Mechanical Services describes various general requirements In MEP Construction Work, a contractor to follow when they start executing but not limited to unforeseen work or requirements to accomplish the whole project contract.
The contractor shall supply, install, test and commission the medium voltage switch gears (13.8 KV) as shown and described on the drawings, specification and bill of quantities.
A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).