Fire alarm systems have become increasingly sophisticated and functionally more capable and reliable in recent years. They are designed to fulfill two general requirements: protection of property and assets and protection of life. As a result of state and local codes, the life-safety aspect of fire protection has become a major factor in the last two decades.
Low Voltage Switchgear are familiar to every people since they are the controlling mediators between low voltage utilities and equipment with human beings. Be it a common home DB or an isolator or control centres, they all are being manufactured to use untrained people ie., common people. The scope of works shall cover the supply installation, testing and commissioning of main and sub-distribution boards, panel boards, fusible safety switches, circuit breakers etc. Associated minor building works require for the erection of the distribution boards and panels shall be included in the scope of work.
Vacuum Interrupter (VI) are vacuum sealed-off devices incorporated in Vacuum Circuit Breakers (VCB) to cause interruption of fault currents in medium voltage electrical distribution systems. The contacts of the VI are pressed against each other under normal circuit conditions. In the event of a fault current, the VCB mechanism effects withdrawal of the movable contact from the fixed contact.
Lightning Protection System should be in accordance with BS 6651 and IEC 61024 to protect the building structure and personnel from the risk of a lightning strike. The installation shall comprise air networks connected to roof and down conductors and finally terminated in earth electrodes, via structural re-bars and suitable test points in accordance with the details included on the attached drawings or in the Specification Section.
Electrical Engineers seldom show interest acquiring knowledge and experience on cable tray installations. Most of them think it's a concern of mechanical fabricators to be taken care of it. A proper and professional way of cable tray installation requires good involvement and coordination of people from both electrical and mechanical disciplines. If cable tray system has been installed appropriately in a project, following advantages can be counted:
A. Protection against Corrosion:
Protect bolted connections against corrosion either hy filling with vaseline or coating with a special anti-corrosion compound and proper capping (Denso tape / grease caps).
Reliable electrical power becomes one of the most wanted factor in modern world industry where operation should be uninterruptible and maximize the cycle of operation, output quality and to avoid losses and damages. Here we are talking about Automatic Transfer Switches (ATS) also known as Automatic Mains Failure (AMF) panel to cater uninterrupted power supply from Mains or backup sources like Diesel gen-set, static ups etc.
This method statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB Panelboards.