Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here.
1. Introduction and Scope
This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Electrical Sub-Main Distribution Boards (SMDB) are the integral part of Electrical LV Power distribution network in the end user premises of a medium and large scale projects. SMDB acts as a mediator between Main Distribution Board (MDB) and Final Distribution Boards (FDB) that serves approximately 100A to 400A load range.
The value is a function of cost. Therefore, it can be increased either by improving the function or reducing cost. The maximum value is achieved when the function performs reliably at the lowest cost. A key principle of value engineering that basic functions be preserved and not reduced as a result of improvements in value. Thus Value Engineering (VE) is a systematic method to improve the "value" of goods, products or services through an examination of the function.
Method of Earthing To Main Distribution Board (MDB)
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.
We often depends Diesel Electrical Genset as emergency power system due to mains failure. As a professional, the installation of diesel electrical power generator should be as per the clients requirement and to be inline with the authoritative norms and standards. Safety, security, convenience, future expansions etc are to be considered and co-ordinated before start detailing of the genset's installation. The generator should be as close to the main change-over board as possible. In cases like Textile Mills, where there is fear of smoke affecting the quality of the yarn etc., generators may be located away from the Plant / Department.
Construction projects highly depends on typical installation details and drawings. Architects and engineers use this kind of information to reduce their work load. Employees particularly technicians and foremen who execute the project uses typical drawings as general guidelines where repeated structure, forms, shapes, operations, loads, etc. come into force.
Construction companies normally submit Payment application every month as per the contract agreement. Until completion of the project, they get part payment from their client after submission of claim which is duly approved and certified by project consultant. Project QS collect all the relevant work details and progress percentage from the field engineers in close coordination with Project Manager.
In this sample MEP specification section, Mechanical Ductwork, Grilles And Diffusers have been described in detail under construction contract work.
Main Highlights of this MEP Specification
- Mechanical Ductwork
- Mechanical Ductwork Supports
- Mechanical Dampers - General Requirements
- Flexible Joints for Mechanical Ductwork
- Air Intakes and Outlets
- Kitchen Extract Canopies
- Kitchen Extract Air Ductwork
- Access Doors
- Ductwork Test Points
- Ductwork Protection
- Sand Trap Louvres
- Air Valves
- Fire Dampers
Lighting Distribution Boards (LDB) are an integral and essential part of every building project and it must be designed, manufactured and installed all in accordance with the safety standards. In most of the cases it operates a layman wherein others operate dedicated or trained person. This article explains what are the essential standards, parts, frame to be applied for manufacturing and installation of lighting distribution boards in a quality building project.
Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
Earthing or Grounding Electrode for an effective and reliable electrical earthing system requires proper survey and analysis of project location, type of structures installed and electrical / electronic equipment used in the entire system. The design calculation of the earth electrode systems shall be based on the approved earth resistivity data and the system's fault currents and their duration.
In this sample MEP specification section, Mechanical General Plant and Machines have been described in detail under construction contract work.
Clean earth grounding or low noise earth shall be provided as required, to ensure that the level of induced or conducted interference from external sources, including the facility power grounding system, does not produce incidence of malfunction of the equipment, which is unacceptable for the operating system. The electronics systems must be protected by providing a network path having low impedance for interconnecting its equipment.
Proper routing, zoning and shielding of the cables / earth wires are important and must serve the purpose of preventing sources of electrical disturbances from the operation of electrical equipment.
Building projects requires MV Distribution Panel Boards for distribution of power to each utilities. A good electrical distribution network will have proper design, right components, and future load provisions. Space utilization will also be an important factor for maintenance and handling of the equipment. Here we look into what are the features required for design, manufacture, install a MV Distribution panel board including its BIS (IS) standards that serving quality building projects.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors. Conduit end to be taken out of the wall above false ceiling to allow the Firetuff cable to be clipped on soffit of the slab.
Drawing below shows how to install Manual call point break glass along with a sounder
In this typical drawing, manual call point break glass unit has been shown as concealed and the rest are surface installed in the false ceiling. Sounder has been mounted on ceiling but can also be mounted on wall visibly as per the project specification.
Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipment luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipment, control gears and poles.