Low Voltage Switchgear are familiar to every people since they are the controlling mediators between low voltage utilities and equipment with human beings. Be it a common home DB or an isolator or control centres, they all are being manufactured to use untrained people ie., common people. The scope of works shall cover the supply installation, testing and commissioning of main and sub-distribution boards, panel boards, fusible safety switches, circuit breakers etc. Associated minor building works require for the erection of the distribution boards and panels shall be included in the scope of work.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors.
The metallic sheath and armour of multicore cables shall be bonded together and earthed. Cable earthing conductors shall be copper strip with appropriate section laid in formed cable trenches or ducts, or fixed to walls, concrete or steel work, by means of clamps or claw type cleats, appropriately secured into suitable wall plugs or tapped holes. The spacing of fixings shall not be greater than 1 m.
In electrical projects, both construction as well as maintenance, the following terms used on the Drawings, Specifications and in the actual Work site are equivalent and may be used interchangeably: "earth" and "ground"; "earthing" and "grounding". Besides, this article tries to rectify misinterpretation of some important terms often used by people involved in the electrical earthing / grounding work.
In this sample MEP specification section, Air Conditioning And Ventilation Installations have been described in detail under construction contract work. All individual components of packaged air handling units shall comply with the appropriate Sections of this Specification unless otherwise specified within the Schedules or on the drawings.