Drawing means lines, shapes, finishes, sizes and colour combined to construct objects or structures. It will be a cumbersome task when narrating an idea without drawing, if the idea is an object or structure. Engineering is heavily depending on drawings, since, technical drawing has developed a global language named Engineering Drawing, capable to express its objects and structure to everyone without the barrier of human languages. Engineering Drawings conveniently helps to explain and record an idea that can be smoothly conveyed to one person to other or sometimes to machine too.
In this sample MEP specification section, Mechanical Refrigeration Plant has been described in detail under construction contract work. Main Highlights of this MEP Specification are: General Requirements, Compressors, Evaporators, Condensers, Condensing Units, Refrigeration Plant Accessories, Pipework, Valves and Ancillaries, Insulation, and Controls.
Method Statement For Installation Of Electrical PVC Conduits And Accessories In The Concrete Slabs, Columns, Block Works And Concrete Walls
1. Introduction and Scope
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls.
Most Construction projects requires underground cabling system for its power supply, some times High tension system too. The architects and builders are least bothered about how this cables routed to the premises and equipment. If electrical professionals pointed out the feasibility, the aesthetics of the project would touch to the intended level. Hence, in the planning stage itself the routes and size of the power cable trench to be incorporated in the project design.
The contractor shall supply, installation, test and commission a public address system consisting of power amplifier, mixer power amplifier, microphone module, paging console, cabinet rack, conduits and wiring and all the necessary equipment required by the system shown and described on drawings, bill of quantities and hereinafter.
It will be the Developers responsibility to obtain all necessary approvals from Authorities having jurisdiction for temporary connections to existing infrastructure. Temporary utilities shall be installed in such a manner as not to interfere with permanent construction. The Plot Developer shall provide any temporary holes or sleeves required to install the temporary utilities and shall be responsible to fill the same upon removal of utilities.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here.
1. Introduction and Scope
This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Capacitor banks help to improve the quality of the electrical power and gives us the more efficient operation of the power system. Capacitor banks are inexpensive if we compare the benefits they deliver to overall power system and can be easily installed anywhere on the network. Automatic Power-factor Correction (APFC) Capacitor Banks also known as Shunt Capacitor Banks (SCB) are installed to provide reactive compensation and power factor correction. The use of APFC improve voltage regulation, saves power loss and improve transmission capabilities.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
In this sample MEP specification section, Mechanical General Plant and Machines have been described in detail under construction contract work.
Clean earth grounding or low noise earth shall be provided as required, to ensure that the level of induced or conducted interference from external sources, including the facility power grounding system, does not produce incidence of malfunction of the equipment, which is unacceptable for the operating system. The electronics systems must be protected by providing a network path having low impedance for interconnecting its equipment.
Proper routing, zoning and shielding of the cables / earth wires are important and must serve the purpose of preventing sources of electrical disturbances from the operation of electrical equipment.
The work included within this section is for the supply, connection, testing and commissioning of 13.8 KV switch gears, cables, package sub station and all the related accessories necessary for the proper operation of the system as shown and described on drawings, bill of quantity and herein.
The contractor shall coordinate with the other services (trades) involved in the project to insure that the foundation, are suitable for the equipment to be installed.
Building projects requires MV Distribution Panel Boards for distribution of power to each utilities. A good electrical distribution network will have proper design, right components, and future load provisions. Space utilization will also be an important factor for maintenance and handling of the equipment. Here we look into what are the features required for design, manufacture, install a MV Distribution panel board including its BIS (IS) standards that serving quality building projects.
Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.
Engineering and Technologies are, in the first instance, simply extensions of the human body, allowing us to overcome the physical limitations with which we are born, and to adapt the natural environment to our own needs. Technologies are inventions of humans that have allowed us to survive, and have enabled our cultures to advance. They are for the most part material objects: tools, for example, are simply detachable additions to the body, the manufacture of which generally distinguishes humans from animals.