We often depends Diesel Electrical Genset as emergency power system due to mains failure. As a professional, the installation of diesel electrical power generator should be as per the clients requirement and to be inline with the authoritative norms and standards. Safety, security, convenience, future expansions etc are to be considered and co-ordinated before start detailing of the genset's installation. The generator should be as close to the main change-over board as possible. In cases like Textile Mills, where there is fear of smoke affecting the quality of the yarn etc., generators may be located away from the Plant / Department.
In this sample MEP specification section, Mechanical Ductwork, Grilles And Diffusers have been described in detail under construction contract work.
Main Highlights of this MEP Specification
- Mechanical Ductwork
- Mechanical Ductwork Supports
- Mechanical Dampers - General Requirements
- Flexible Joints for Mechanical Ductwork
- Air Intakes and Outlets
- Kitchen Extract Canopies
- Kitchen Extract Air Ductwork
- Access Doors
- Ductwork Test Points
- Ductwork Protection
- Sand Trap Louvres
- Air Valves
- Fire Dampers
Vacuum Interrupter (VI) are vacuum sealed-off devices incorporated in Vacuum Circuit Breakers (VCB) to cause interruption of fault currents in medium voltage electrical distribution systems. The contacts of the VI are pressed against each other under normal circuit conditions. In the event of a fault current, the VCB mechanism effects withdrawal of the movable contact from the fixed contact.
The scope of work shall cover providing grounding stations, laying copper ground wires and connecting the panels, equipment, etc. to the ground grip as shown in the drawing.
Earth / Ground Station
The ground station shall be as shown in the drawing. The ground electrode shall be minimum 10 feet long 1 inch dia steel pipe with copper weld exterior surface. The ground resistance shall be maintained with a suitable soil treatment as shown on drawings or as discussed and decided at site.
The resistance of each ground shall not exceed 2 ohms.
The ground wire shall be fixed to the rod with a clamp and safety set screws. The clamp shall be permanently accessible. Manholes with proper covers shall be provided.
Ground connections shall be of the bolted type on the top of the rod.
Earthing / Grounding work has to comply with the requirements of General and Technical Conditions of the Project including statutory obligations and regulations. Submittals to be approved by project consultant prior execution of the actual work. Regulations and rules of supply authority also to be considered when preparing the submittals for the local in which installation is being constructed.
Signal and Communication Systems: For telephone, alarm, voice and data, and other communication systems, provide 16 mm2 minimum insulated grounding conductor in raceway from a separate grounding electrode clean system to each service location, terminal cabinet, wiring closet, and central equipment location.
Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
Drawing means lines, shapes, finishes, sizes and colour combined to construct objects or structures. It will be a cumbersome task when narrating an idea without drawing, if the idea is an object or structure. Engineering is heavily depending on drawings, since, technical drawing has developed a global language named Engineering Drawing, capable to express its objects and structure to everyone without the barrier of human languages. Engineering Drawings conveniently helps to explain and record an idea that can be smoothly conveyed to one person to other or sometimes to machine too.
In this sample MEP specification section, Mechanical Refrigeration Plant has been described in detail under construction contract work. Main Highlights of this MEP Specification are: General Requirements, Compressors, Evaporators, Condensers, Condensing Units, Refrigeration Plant Accessories, Pipework, Valves and Ancillaries, Insulation, and Controls.
The contractor shall supply, installation, test and commission a public address system consisting of power amplifier, mixer power amplifier, microphone module, paging console, cabinet rack, conduits and wiring and all the necessary equipment required by the system shown and described on drawings, bill of quantities and hereinafter.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here.
1. Introduction and Scope
This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Capacitor banks help to improve the quality of the electrical power and gives us the more efficient operation of the power system. Capacitor banks are inexpensive if we compare the benefits they deliver to overall power system and can be easily installed anywhere on the network. Automatic Power-factor Correction (APFC) Capacitor Banks also known as Shunt Capacitor Banks (SCB) are installed to provide reactive compensation and power factor correction. The use of APFC improve voltage regulation, saves power loss and improve transmission capabilities.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
In this sample MEP specification section, Mechanical General Plant and Machines have been described in detail under construction contract work.
The work included within this section is for the supply, connection, testing and commissioning of 13.8 KV switch gears, cables, package sub station and all the related accessories necessary for the proper operation of the system as shown and described on drawings, bill of quantity and herein.
The contractor shall coordinate with the other services (trades) involved in the project to insure that the foundation, are suitable for the equipment to be installed.
The Contractor shall design, supply and install outlet plates, conduits, trunking, trays, wiring, junction boxes, distribution frames, patch panels, data rack, backbone cables, etc. necessary to form a complete structured system for voice and data cabling within the buildings. Cabling / wiring shall be provided for voice system from patch panel location to each voice/data outlet. Draw wires shall be provided in conduits for future data cabling / wiring by others (if applicable). The installation shall comply with the requirements of ANSI / EIA / TIA-568-1991 as appropriate as well as Local Telecom Authority.
Voice and data outlet plates shall be designed to accept industry standard RJ45 plugs.