A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
The company standard procedures will be implemented for the project however should a situation arise where this may be detrimental to the project or where an improvement could be made to a standard procedure the Project Manager shall be notified. With agreement of the Quality Assurance Manager a project procedure may be established and thus added to the Quality plan.
Electrical Earthing or Grounding System for buildings to be carried out all in accordance with the international standards in conjunction with the local authority requirements and recommendations. Earthing standards and methods are highly depending on the nature of the utilities and equipment installed / used at the premises. Simple earthing system we provide to the domestic connections while complex systems are being used in the power stations and industries.
Reliable electrical power becomes one of the most wanted factor in modern world industry where operation should be uninterruptible and maximize the cycle of operation, output quality and to avoid losses and damages. Here we are talking about Automatic Transfer Switches (ATS) also known as Automatic Mains Failure (AMF) panel to cater uninterrupted power supply from Mains or backup sources like Diesel gen-set, static ups etc.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.