The contractor shall supply, install, test and commission the medium voltage switch gears (13.8 KV) as shown and described on the drawings, specification and bill of quantities.
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls. This method statement should be used for both inside and out side the building.
Scope of Work of this this sample specification covers the supply, installation, testing and commissioning of all wiring materials for power and lighting in concealed and/or surface conduits.
1. Applicable Standards
The conduits shall conform to IS 9537 I & II or equivalent standards. Switches, Plug Sockets shall conform to IS 3854 and IS 4615, however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here. This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
The scope of this specification covers the supply, installation and testing and earthing system of the entire installation and for lightning protection.
This method of statement specifies the detailed requirements and procedures for the installation of Power and Lighting System Wiring. Installation: No wiring be carried out until the appropriate tests required or in the electrical testing section have been done and the consultant has given his clearance for wiring to commence. A loop in form of wiring shall be used as far as practicable or unless otherwise indicated. Joints in conductors shall be made using insulated terminal blocks complying with requirements of this specification.