Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
1. Introduction and Scope
This method statement is written for the purpose of establishing method and procedures for the Installation of DB, SMDB and MDB Panelboards.
2. Applicable Projects Specification
Section: SWITCHBOARD DISTRIBUTION PANELS AND MCCs.
Sub Division: Subdivision
3. Location of Activity
Low Voltage Room and Electrical Rooms
Earthing or Grounding Electrode for an effective and reliable electrical earthing system requires proper survey and analysis of project location, type of structures installed and electrical / electronic equipment used in the entire system. The design calculation of the earth electrode systems shall be based on the approved earth resistivity data and the system's fault currents and their duration.
Drawing means lines, shapes, finishes, sizes and colour combined to construct objects or structures. It will be a cumbersome task when narrating an idea without drawing, if the idea is an object or structure. Engineering is heavily depending on drawings, since, technical drawing has developed a global language named Engineering Drawing, capable to express its objects and structure to everyone without the barrier of human languages. Engineering Drawings conveniently helps to explain and record an idea that can be smoothly conveyed to one person to other or sometimes to machine too.
In this sample MEP specification section, Mechanical Refrigeration Plant has been described in detail under construction contract work. Main Highlights of this MEP Specification are: General Requirements, Compressors, Evaporators, Condensers, Condensing Units, Refrigeration Plant Accessories, Pipework, Valves and Ancillaries, Insulation, and Controls.
The contractor shall supply, installation, test and commission a public address system consisting of power amplifier, mixer power amplifier, microphone module, paging console, cabinet rack, conduits and wiring and all the necessary equipment required by the system shown and described on drawings, bill of quantities and hereinafter.
Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here.
1. Introduction and Scope
This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
Capacitor banks help to improve the quality of the electrical power and gives us the more efficient operation of the power system. Capacitor banks are inexpensive if we compare the benefits they deliver to overall power system and can be easily installed anywhere on the network. Automatic Power-factor Correction (APFC) Capacitor Banks also known as Shunt Capacitor Banks (SCB) are installed to provide reactive compensation and power factor correction. The use of APFC improve voltage regulation, saves power loss and improve transmission capabilities.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
Electrical Sub-Main Distribution Boards (SMDB) are the integral part of Electrical LV Power distribution network in the end user premises of a medium and large scale projects. SMDB acts as a mediator between Main Distribution Board (MDB) and Final Distribution Boards (FDB) that serves approximately 100A to 400A load range.
The work included within this section is for the supply, connection, testing and commissioning of 13.8 KV switch gears, cables, package sub station and all the related accessories necessary for the proper operation of the system as shown and described on drawings, bill of quantity and herein.
The contractor shall coordinate with the other services (trades) involved in the project to insure that the foundation, are suitable for the equipment to be installed.
The Contractor shall design, supply and install outlet plates, conduits, trunking, trays, wiring, junction boxes, distribution frames, patch panels, data rack, backbone cables, etc. necessary to form a complete structured system for voice and data cabling within the buildings. Cabling / wiring shall be provided for voice system from patch panel location to each voice/data outlet. Draw wires shall be provided in conduits for future data cabling / wiring by others (if applicable). The installation shall comply with the requirements of ANSI / EIA / TIA-568-1991 as appropriate as well as Local Telecom Authority.
Voice and data outlet plates shall be designed to accept industry standard RJ45 plugs.
Building projects requires MV Distribution Panel Boards for distribution of power to each utilities. A good electrical distribution network will have proper design, right components, and future load provisions. Space utilization will also be an important factor for maintenance and handling of the equipment. Here we look into what are the features required for design, manufacture, install a MV Distribution panel board including its BIS (IS) standards that serving quality building projects.
Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.