Signal and Communication Systems: For telephone, alarm, voice and data, and other communication systems, provide 16 mm2 minimum insulated grounding conductor in raceway from a separate grounding electrode clean system to each service location, terminal cabinet, wiring closet, and central equipment location.
In this sample MEP specification section, Mechanical Refrigeration Plant has been described in detail under construction contract work. Main Highlights of this MEP Specification are: General Requirements, Compressors, Evaporators, Condensers, Condensing Units, Refrigeration Plant Accessories, Pipework, Valves and Ancillaries, Insulation, and Controls.
The contractor shall supply, installation, test and commission a public address system consisting of power amplifier, mixer power amplifier, microphone module, paging console, cabinet rack, conduits and wiring and all the necessary equipment required by the system shown and described on drawings, bill of quantities and hereinafter.
It will be the Developers responsibility to obtain all necessary approvals from Authorities having jurisdiction for temporary connections to existing infrastructure. Temporary utilities shall be installed in such a manner as not to interfere with permanent construction. The Plot Developer shall provide any temporary holes or sleeves required to install the temporary utilities and shall be responsible to fill the same upon removal of utilities.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
The work included within this section is for the supply, connection, testing and commissioning of 13.8 KV switch gears, cables, package sub station and all the related accessories necessary for the proper operation of the system as shown and described on drawings, bill of quantity and herein.
The contractor shall coordinate with the other services (trades) involved in the project to insure that the foundation, are suitable for the equipment to be installed.
Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.
Engineering and Technologies are, in the first instance, simply extensions of the human body, allowing us to overcome the physical limitations with which we are born, and to adapt the natural environment to our own needs. Technologies are inventions of humans that have allowed us to survive, and have enabled our cultures to advance. They are for the most part material objects: tools, for example, are simply detachable additions to the body, the manufacture of which generally distinguishes humans from animals.
Audio Intercom System being used in high-rise buildings or commercial complexes, provide two way communication from entrances, gates, go-downs, industrial plant rooms and normal doors, to an internal audio handset. It can be used to screen authorized visitors from outside entrance and useful to communicate internally between persons from one room to another room or office spaces. It can also be used to function as effective public announcement system.
The contractor shall supply, install, test and commission the 13.8 KV cable network as shown and indicated on the contract documents. Conductor sizes shall be metric as shown, conductor sizes with cross sectional areas smaller than specified will not be accepted. The cable installation shall include all trench work, sleeves, ducts, and all necessary fixings and cable terminations at both ends of the cable. The contractor shall supply and install cable marker posts to indicate the route of all underground cables. Markers shall be provided at every bend along the route and at sites of crossing roads or pipe lines.
WiMAX Broadband Internet is an IP based Wireless Broadband Access Technology utilizing IEEE 802.16e-2005 standard as the air interface. WiMAX will provide broadband connectivity anywhere, anytime, for any device and on any network. WiMAX is a unique technology being deployed by BSNL for the first time in India.
Special areas like Airports, Port Trusts, Naval Base, Military base, Telecom buildings, Refinery, Petroleum handling areas etc. needed highly sophisticated security and access control system. It provides safety and security for both men and equipment the area handling. Here is the specification and installation methods for SACS.
This article explains electrical power cables used in construction works complete with supply, installation, testing and commissioning of High Voltage (HV) and Low Voltage (LV) cables. All cables shall conform to standards of IS 7098-1973, IS 1554-1976 and wiring cables to IS 694-1977 however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Continuity: Ensure that complete earthing system is electrically continuous and mechanically secure. Locations of main earth bars in substations, electrical rooms, mechanical rooms, hub (Technical) rooms, etc., to be clearly identified by 100mm X 100mm white traffolyte labels, with red lettering, to Engineer's approval.
Electrical engineering deals with practical applications involving current flow through conductors; focuses on the design, construction, and operation of electrical systems and equipment. It includes developing, producing and testing of electrical and electronic devices and equipment, such as, generators to produce and distribute electricity, electric motors and other electrical machinery, transmission line.
Fire Alarm System installation work covered by this section of the specifications includes the furnishing of all labor, equipment, materials, and performance of all operations in connection with the whole Fire Alarm System as shown on the drawings and as herein specified. The requirements of the conditions of the Contract, Supplementary Conditions and General Requirements apply to the work specified in this section.