Building projects requires MV Distribution Panel Boards for distribution of power to each utilities. A good electrical distribution network will have proper design, right components, and future load provisions. Space utilization will also be an important factor for maintenance and handling of the equipment. Here we look into what are the features required for design, manufacture, install a MV Distribution panel board including its BIS (IS) standards that serving quality building projects.
This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.
Engineering and Technologies are, in the first instance, simply extensions of the human body, allowing us to overcome the physical limitations with which we are born, and to adapt the natural environment to our own needs. Technologies are inventions of humans that have allowed us to survive, and have enabled our cultures to advance. They are for the most part material objects: tools, for example, are simply detachable additions to the body, the manufacture of which generally distinguishes humans from animals.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors. Conduit end to be taken out of the wall above false ceiling to allow the Firetuff cable to be clipped on soffit of the slab.
Drawing below shows how to install Manual call point break glass along with a sounder
In this typical drawing, manual call point break glass unit has been shown as concealed and the rest are surface installed in the false ceiling. Sounder has been mounted on ceiling but can also be mounted on wall visibly as per the project specification.
Audio Intercom System being used in high-rise buildings or commercial complexes, provide two way communication from entrances, gates, go-downs, industrial plant rooms and normal doors, to an internal audio handset. It can be used to screen authorized visitors from outside entrance and useful to communicate internally between persons from one room to another room or office spaces. It can also be used to function as effective public announcement system.
The contractor shall supply, install, test and commission the 13.8 KV cable network as shown and indicated on the contract documents. Conductor sizes shall be metric as shown, conductor sizes with cross sectional areas smaller than specified will not be accepted. The cable installation shall include all trench work, sleeves, ducts, and all necessary fixings and cable terminations at both ends of the cable. The contractor shall supply and install cable marker posts to indicate the route of all underground cables. Markers shall be provided at every bend along the route and at sites of crossing roads or pipe lines.
WiMAX Broadband Internet is an IP based Wireless Broadband Access Technology utilizing IEEE 802.16e-2005 standard as the air interface. WiMAX will provide broadband connectivity anywhere, anytime, for any device and on any network. WiMAX is a unique technology being deployed by BSNL for the first time in India.
The scope of work shall cover laying, connecting, testing and commissioning of low voltage power cables complete with all cable support, cable, cable trays, clamps and joints. Cables to be purchased from who regularly engaged in the manufacturer of electrical cable and wire products of the types and ratings required, whose products have been in satisfactory use in similar service not less than 5 years. The standard of the cables shall comply with National Electrical Manufacturers Association of local standards or any other approved.
Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipment luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipment, control gears and poles.
Modern Buildings essentially implement the needs of Diesel Powered Electricity Generation Plant. It would become an integral part of the building the day building occupied by its tenants. Here we look into what are the objectives, specifications, services to be considered for functioning complete Diesel Powered Electricity Generation Plant installed in a commercial Building.
Method of Earthing To Main Distribution Board (MDB)
Main earthing bar is to be provided in main distribution room and connected to earth electrode by 2 insulated conductors (minimum 150 mm2) via testing joints. Earthing bars of main distribution boards are to be connected, by insulated earthing conductor, directly to main earthing bar at main distribution room.
Special areas like Airports, Port Trusts, Naval Base, Military base, Telecom buildings, Refinery, Petroleum handling areas etc. needed highly sophisticated security and access control system. It provides safety and security for both men and equipment the area handling. Here is the specification and installation methods for SACS.
This article explains electrical power cables used in construction works complete with supply, installation, testing and commissioning of High Voltage (HV) and Low Voltage (LV) cables. All cables shall conform to standards of IS 7098-1973, IS 1554-1976 and wiring cables to IS 694-1977 however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.
Occasionally Main Contractor of the construction work depends sub-contractor for accomplishing some smaller or part of the project that may require specialized technical know-how and installation methods. In those cases Main contractor selects some sub-contractors who has capacity to achieve the task within the given time frame. Hence both of the parties, ie., Main contractor and Sub-contractor to be signed an agreement which protects both the parties' interest. Here is a sample for Conditions of Sub-contract Agreement in Construction Works.
In this sample MEP specification section, Mechanical Fire Fighting Services have been described in detail under construction contract work. Main Highlights of this MEP Specification for Fire Fighting Services are: Pipework Generally, Dry Risers, Hose Reels, Fire Hydrants and Sprinkler Installation.
Continuity: Ensure that complete earthing system is electrically continuous and mechanically secure. Locations of main earth bars in substations, electrical rooms, mechanical rooms, hub (Technical) rooms, etc., to be clearly identified by 100mm X 100mm white traffolyte labels, with red lettering, to Engineer's approval.
This specification intended to supply, install, test and commission mineral oil immersed 1500 KVA, 3 phase indoor transformers, fitted with cable boxes, bolts, and all necessary accessories. Transformers shall be indoor type, oil filled, two winding, four off load capacity, 2.5% taps, two above and two below high voltage rating in compliance with IEC 76 or BS 171.
Electrical engineering deals with practical applications involving current flow through conductors; focuses on the design, construction, and operation of electrical systems and equipment. It includes developing, producing and testing of electrical and electronic devices and equipment, such as, generators to produce and distribute electricity, electric motors and other electrical machinery, transmission line.
The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.