Construction companies normally submit Payment application every month as per the contract agreement. Until completion of the project, they get part payment from their client after submission of claim which is duly approved and certified by project consultant. Project QS collect all the relevant work details and progress percentage from the field engineers in close coordination with Project Manager.
Every project is unique, in particular, construction projects. There are many methods applied to accomplish functioning of individual installations included in the whole project. Building services like Mechanical, Electric, and Plumbing (MEP) work have given more importance than other disciplines dealt with. It's because of complexity and alternate methods available to accomplish the same output. While executing individual installations - also known as tasks - construction team have to adopt suitable methods submitted as an integral part of Tender. Most of the project managers or representatives of client keen to look Method Statement of critical and important tasks. We will look into what is Method Statement and what is the importance a Method Statement brings to a construction project.
The scope of work shall cover providing grounding stations, laying copper ground wires and connecting the panels, equipment, etc. to the ground grip as shown in the drawing.
Earth / Ground Station
The ground station shall be as shown in the drawing. The ground electrode shall be minimum 10 feet long 1 inch dia steel pipe with copper weld exterior surface. The ground resistance shall be maintained with a suitable soil treatment as shown on drawings or as discussed and decided at site.
The resistance of each ground shall not exceed 2 ohms.
The ground wire shall be fixed to the rod with a clamp and safety set screws. The clamp shall be permanently accessible. Manholes with proper covers shall be provided.
Ground connections shall be of the bolted type on the top of the rod.
In electrical projects, both construction as well as maintenance, the following terms used on the Drawings, Specifications and in the actual Work site are equivalent and may be used interchangeably: "earth" and "ground"; "earthing" and "grounding". Besides, this article tries to rectify misinterpretation of some important terms often used by people involved in the electrical earthing / grounding work.