The contractor shall supply, install, test and commission the 13.8 KV cable network as shown and indicated on the contract documents. Conductor sizes shall be metric as shown, conductor sizes with cross sectional areas smaller than specified will not be accepted. The cable installation shall include all trench work, sleeves, ducts, and all necessary fixings and cable terminations at both ends of the cable. The contractor shall supply and install cable marker posts to indicate the route of all underground cables. Markers shall be provided at every bend along the route and at sites of crossing roads or pipe lines.
This article covers the manufacture, supply, installation, testing and commissioning of 415 volts, 3 ph, 4 wire, Diesel Alternator Set (Diesel Genset). The set shall be mounted on common base frame and complete in all respects including the auxiliary equipment such as battery auxiliary, lube oil pumps, filters, oil storage tank, centrifuge, etc. including piping required for interconnection between the set and the auxiliaries which are mounted separately.
This specification intended to supply, install, test and commission mineral oil immersed 1500 KVA, 3 phase indoor transformers, fitted with cable boxes, bolts, and all necessary accessories. Transformers shall be indoor type, oil filled, two winding, four off load capacity, 2.5% taps, two above and two below high voltage rating in compliance with IEC 76 or BS 171.