MV switchgear and MV cables are to have separate main earthing bar connected to framework or earth bar of each item by insulated conductor and the earth-electrode by 2 insulated earthing conductors, one at each end of bar, via testing joints. Earthing conductor is to be minimum 150 mm2.
LV switchgear is to have separate main earthing bar connected to framework or earth bar of each item by insulated conductor.
Main LV switchgear panel is connected to main LV Earth bar in electrical room which in tum connected at two ends by 2 insulated earthing conductors through testing joints to two earth pits. Earthing conductor size is to be minimum 150 mm2.
Transformer body earthing terminal is to be connected to MV main earthing bar by insulated copper earthing conductor not less than 20 mm2 per 100 kVA of transformer rating, with a minimum of 35 mm2.
Transformer neutral (star point) is to be connected by insulated earthing conductor (colour black) directly to independent earthing electrode. Neutral earthing conductor is to be sized for maximum earth fault current for 5 seconds with final conductor temperature not exceeding 160 deg. C or sized not less than 30 mm2 per 100 kVA of transformer rating, and with a minimum of 50 mm2.
Lightning arresters are to be directly connected to the earth electrode, following the shortest path. Each lightning arrester is to be connected at a dedicated earth rod.