Method Statement For Installation Of Galvanized Conduits that has to be installed on the Exposed Surface of a building is described here. This method of statement specify the detailed requirements and procedures for the installation of Galvanized Conduits for the exposed surface installation requirement for MEP services of the above building.
This method statement explains the detailed requirements and procedures for the installation of PVC Conduits and accessories in the concrete slabs, columns, block works and concrete walls. This method statement should be used for both inside and out side the building.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors.
Scope of Work of this this sample specification covers the supply, installation, testing and commissioning of all wiring materials for power and lighting in concealed and/or surface conduits.
1. Applicable Standards
The conduits shall conform to IS 9537 I & II or equivalent standards. Switches, Plug Sockets shall conform to IS 3854 and IS 4615, however, contractor shall comply with the latest or superseded versions of IS/BIS to be used for the complete work.