Signal and Communication Systems: For telephone, alarm, voice and data, and other communication systems, provide 16 mm2 minimum insulated grounding conductor in raceway from a separate grounding electrode clean system to each service location, terminal cabinet, wiring closet, and central equipment location.
Clean earth grounding or low noise earth shall be provided as required, to ensure that the level of induced or conducted interference from external sources, including the facility power grounding system, does not produce incidence of malfunction of the equipment, which is unacceptable for the operating system.
Earthing or Grounding Electrode for an effective and reliable electrical earthing system requires proper survey and analysis of project location, type of structures installed and electrical / electronic equipment used in the entire system. The design calculation of the earth electrode systems shall be based on the approved earth resistivity data and the system's fault currents and their duration.
Earthing / Grounding work has to comply with the requirements of General and Technical Conditions of the Project including statutory obligations and regulations. Submittals to be approved by project consultant prior execution of the actual work. Regulations and rules of supply authority also to be considered when preparing the submittals for the local in which installation is being constructed.