A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
Electrical Earthing or Grounding System for buildings to be carried out all in accordance with the international standards in conjunction with the local authority requirements and recommendations. Earthing standards and methods are highly depending on the nature of the utilities and equipment installed / used at the premises. Simple earthing system we provide to the domestic connections while complex systems are being used in the power stations and industries.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
In electrical projects, both construction as well as maintenance, the following terms used on the Drawings, Specifications and in the actual Work site are equivalent and may be used interchangeably: "earth" and "ground"; "earthing" and "grounding". Besides, this article tries to rectify misinterpretation of some important terms often used by people involved in the electrical earthing / grounding work.