The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
Signal and Communication Systems: For telephone, alarm, voice and data, and other communication systems, provide 16 mm2 minimum insulated grounding conductor in raceway from a separate grounding electrode clean system to each service location, terminal cabinet, wiring closet, and central equipment location.
A. Earthing Cables: Separate protective earthing cables for lighting column circuits are to be run with power circuit, terminated at LV supply position in lighting control panel and looped into column earthing terminals. The last column is to be bonded via an earthing bolt to a single 16 mm diameter stainless steel rod, 3.6 m long, driven into ground adjacent to column. Bonding is to be 16 mm2 stranded bare copper conductor.
Earth electrode resistance, Insulation resistance of factory-built materials installed at the site and Insulation resistance of site-built materials installed at site to be considered individually for field quality control check. It is further to be monitored earth resistance of individual earth unit and combined resistance of earth units.
Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipment luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipment, control gears and poles.
Audio Intercom System being used in high-rise buildings or commercial complexes, provide two way communication from entrances, gates, go-downs, industrial plant rooms and normal doors, to an internal audio handset. It can be used to screen authorized visitors from outside entrance and useful to communicate internally between persons from one room to another room or office spaces. It can also be used to function as effective public announcement system.
Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
Electrical Earthing or Grounding System for buildings to be carried out all in accordance with the international standards in conjunction with the local authority requirements and recommendations. Earthing standards and methods are highly depending on the nature of the utilities and equipment installed / used at the premises. Simple earthing system we provide to the domestic connections while complex systems are being used in the power stations and industries.
Master Antenna Television or MATV means many TV connection outlets from one Master antenna control system. Usually high-rise apartment houses, hotels, schools and cluster based residential area utilizes this kind of TV distribution network. It may or may not include FM radio so that one outlet can receive both TV and FM reception. The scope of this section covers the design, supply, installation, testing and commissioning of Master Antenna TV System, for the reception and distribution of television broadcast signals.