The acronym MEP became an integral word of a building project in Middle East Gulf region during year 2000. In the inception stage of MEP, there were involvement of only two engineering branches, Mechanical and Electrical, now it included electronics, instrumentation and communication. In some occasions, Mechatronics also partake in the project for smooth completion of the whole MEP works. Companies that carry out MEP works also known as Electro-Mechanical company which has multi-faceted technicians and engineers for effective design, coordination and execution of the works.
A. Main earthing bar or loop is to be conveniently located in electrical/mechanical plant rooms, and connected by earthing conductors to exposed conductive parts of motor control centre at its earthing bar, and to motors, switches and other electrical equipment etc. at their earthing terminals, using 20 x 2 mm insulated copper strips or 35 mm2 insulated copper conductor (minimum size) or as required to carry maximum earth fault current for 1 second with final conductor temperature not exceeding 200 deg. C (392 deg. F).
Electrical Earthing or Grounding System for buildings to be carried out all in accordance with the international standards in conjunction with the local authority requirements and recommendations. Earthing standards and methods are highly depending on the nature of the utilities and equipment installed / used at the premises. Simple earthing system we provide to the domestic connections while complex systems are being used in the power stations and industries.
Earthing or Grounding of Diesel Generator Plant is important to ensure correct operation of the plant and safety of the people who work over there. Generator neutral (star point) is to be connected by insulated earthing conductor through the neutral earthing link or device to main earthing bar. Neutral earthing conductor is to be suitably sized to carry maximum earth fault current for time it takes the system protection to operate with final conductor temperature not exceeding 160 deg. C, but not less than 30 mm2 per 100 kVA of generator rating, with a minimum of 50 mm2. All emergency power diesel gensets including portable gensets to be connected to grounding conductor.
A. Ground Rod:
16 mm diameter stainless steel. Driving head is to be high strength steel. Couplings are to be long length silicon bronze, internally threaded. Threads are to be rolled onto rod to ensure uniform layers of copper and strength. Earth rod is to be complete with non-corrosive couplings, head and bolted connector of sufficient size, and number of bolted clamps to connect all cables terminated thereto.
In electrical projects, both construction as well as maintenance, the following terms used on the Drawings, Specifications and in the actual Work site are equivalent and may be used interchangeably: "earth" and "ground"; "earthing" and "grounding". Besides, this article tries to rectify misinterpretation of some important terms often used by people involved in the electrical earthing / grounding work.
A. Protection against Corrosion:
Protect bolted connections against corrosion either hy filling with vaseline or coating with a special anti-corrosion compound and proper capping (Denso tape / grease caps).
The metallic sheath and armour of multicore cables shall be bonded together and earthed. Cable earthing conductors shall be copper strip with appropriate section laid in formed cable trenches or ducts, or fixed to walls, concrete or steel work, by means of clamps or claw type cleats, appropriately secured into suitable wall plugs or tapped holes. The spacing of fixings shall not be greater than 1 m.
Capacitor banks help to improve the quality of the electrical power and gives us the more efficient operation of the power system. Capacitor banks are inexpensive if we compare the benefits they deliver to overall power system and can be easily installed anywhere on the network. This specification covers the manufacture, supply, installation, testing and commissioning of 415 Volts, 3 phase, 50 HZ, capacitor banks for power factor improvement in building electrification project.