Technical Submittals of Materials / Equipment Approval for External, Exterior and Outdoor Lighting System consists equipment data, compliance statements, shop drawings or construction drawings, samples, product certificates, field test reports, maintenance data and as-built (record) drawings.
A. Earthing Cables: Separate protective earthing cables for lighting column circuits are to be run with power circuit, terminated at LV supply position in lighting control panel and looped into column earthing terminals. The last column is to be bonded via an earthing bolt to a single 16 mm diameter stainless steel rod, 3.6 m long, driven into ground adjacent to column. Bonding is to be 16 mm2 stranded bare copper conductor.
Installation Methods of External, Exterior and Outdoor Lighting System includes lighting equipment luminaires, control gears, panel boards, poles, brackets, cabling, and allied minor civil works. All installations are to be carried out under strict supervision of qualified supervisors and engineers. If installation required heavy vehicles, extreme care has to be taken for preventing damages of lighting equipment, control gears and poles.