Construction Shop drawings are the actual detail of all manufactured or fabricated items, indicate proper relation to adjoining work, amplify design details of equipment in proper relation to physical spaces in the structure, and incorporate minor changes of design or construction to suit actual conditions.
These drawings show how to install Fire Alarm Break Glass (BG) or Manual Call Point (MCP) on walls. It has to be mounted on back box installed in the wall. This box (embedded or exposed as specified in the concerned section of the specification) has to be connected through GI / PVC conduit that will have the Firetuff or equivalent cable to be looped for other detectors. Conduit end to be taken out of the wall above false ceiling to allow the Firetuff cable to be clipped on soffit of the slab.
Drawing below shows how to install Manual call point break glass along with a sounder
In this typical drawing, manual call point break glass unit has been shown as concealed and the rest are surface installed in the false ceiling. Sounder has been mounted on ceiling but can also be mounted on wall visibly as per the project specification.